L 36 W/865
References / Links
For more information on the system guarantee and the terms and conditions of the guarantee visit www.osram.com/systemguarantee
For more information on QUICKTRONIC electronic control gear go to www.osram.com/QUICKTRONIC
Technical Data
Electrical data
Nominal wattage
36.00 W
Rated lamp efficacy (HF data 25 °C)
Under clarification by authority and standardization body
Rated wattage
36.00 W
Photometrical data
Rated lamp efficacy (standard condition)
90 lm/W
Color rendering index Ra
≥77
Rated luminous flux
3250 lm
Luminous flux at
3250 lm
Light color
765
Rated color temperature
6500 K
Nominal luminous flux
3250 lm
Light color (designation)
LUMILUX Cool Daylight
Rated LLMF at 2,000 h
0.96
Rated LLMF at 4,000 h
0.94
Rated LLMF at 6,000 h
0.93
Rated LLMF at 8,000 h
0.91
Rated LLMF at 12,000 h
0.91
Rated LLMF at 16,000 h
0.90
Rated LLMF at 20,000 h
0.89
Luminous flux
3250 lm
Color temperature
6500 K
Dimensions & weight
Tube diameter
26 mm
Length
1200 mm
Length with base excl. base pins/connection
1200.00 mm
Diameter
26.0 mm
Maximum diameter
26.0 mm
Product weight
149.00 g
Outer bulb
T26
Temperatures & operating conditions
Rated ambient temp.w.max.luminous flux
25.0 °C
Lifespan
Service life
18000 h
Lifespan
20000 h
Rated lamp survival factor at 2,000 h
0.99
Rated lamp survival factor at 4,000 h
0.99
Rated lamp survival factor at 6,000 h
0.99
Rated lamp survival factor at 8,000 h
0.99
Rated lamp survival factor at 12,000 h
0.99
Rated lamp survival factor at 16,000 h
0.99
Rated lamp survival factor at 20,000 h
0.50
Operation mode LLMF/LSF
HF
Rated lamp life time
20000 h
Additional product data
Base (standard designation)
G13
Mercury content
2.5 mg
Appropriate disposal acc. to WEEE
Yes
Capabilities
Dimmable
Yes
Suitable for indoor
Yes
Certificates & standards
Energy consumption
43 kWh/1000h
Energy efficiency class
A
Country specific categorizations
Order reference
L 36W/865
Packaging information
EAN 
Unit 
Piece 
Dimension l x w x h 
Weight 
Volume 

4050300517858 
FLH
 1  1215mm x 27mm x 27mm  177.00g  0.89dm³ 
4050300517865 
VS
 25  142mm x 145mm x 1242mm  4762.00g  25.57dm³ 
Downloads
LampECG Combination
QT 1x36 DIM
Nominal current
0.16 A
Nominal wattage + Power loss
36.00 W
Luminous flux at 35 °C
3350 lm
Number of lighting outlets
1
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
50 °C
ECG_2.2 Tc point temperature for lifespa
60 °C
ECG_2.3 Tc point temperature for lifespa
70 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
100000 h
QT 2x36 DIM
Nominal current
0.32 A
Nominal wattage + Power loss
72.40 W
Luminous flux at 35 °C
3350 lm
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
65 °C
ECG_2.3 Tc point temperature for lifespa
75 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
90000 h
QTFIT 5/8 1x1839
Nominal current
0.16 A
Nominal wattage + Power loss
37.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
1
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
65 °C
ECG_2.3 Tc point temperature for lifespa
75 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
60000 h
ECG_3.3 Temperature dependent lifespan
40000 h
QTFIT 5/8 2x1839
Nominal current
0.31 A
Nominal wattage + Power loss
70.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
65 °C
ECG_2.3 Tc point temperature for lifespa
75 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
60000 h
ECG_3.3 Temperature dependent lifespan
30000 h
QTFIT8 1x36
Nominal current
0.16 A
Nominal wattage + Power loss
36.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
1
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
50 °C
ECG_2.2 Tc point temperature for lifespa
60 °C
ECG_2.3 Tc point temperature for lifespa
65 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
70000 h
QTFIT8 2x36
Nominal current
0.32 A
Nominal wattage + Power loss
71.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
60 °C
ECG_2.3 Tc point temperature for lifespa
70 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
90000 h
ECG_3.3 Temperature dependent lifespan
50000 h
QTi 1x14/24/21/39 GII
QTi 2x14/24/21/39 GII
QTi DALI 1x36 DIM
Nominal current
0.16 A
Nominal wattage + Power loss
36.00 W
Luminous flux at 35 °C
3350 lm
Ambient temperature range [PIM] REM
Operation at up to 20 °C for all QTi (DALI) DIMECG possible. Lowest dimming position must be limited. Details see technical dimming brochure.
Number of lighting outlets
1
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
50 °C
ECG_2.2 Tc point temperature for lifespa
60 °C
ECG_2.3 Tc point temperature for lifespa
70 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
100000 h
QTi DALI 2x36 DIM
Nominal current
0.30 A
Nominal wattage + Power loss
69.00 W
Luminous flux at 35 °C
3350 lm
Ambient temperature range [PIM] REM
Operation at up to 20 °C for all QTi (DALI) DIMECG possible. Lowest dimming position must be limited. Details see technical dimming brochure.
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
65 °C
ECG_2.3 Tc point temperature for lifespa
75 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
90000 h
QTM 2x2642/220240 S
QTPDL 2x3640
QTPM 1x2642
QTPOPTIMAL 1x1840
Nominal current
0.16 A
Nominal wattage + Power loss
36.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
1
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
60 °C
ECG_2.3 Tc point temperature for lifespa
70 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
80000 h
QTPOPTIMAL 2x1840
Nominal current
0.30 A
Nominal wattage + Power loss
71.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
40 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
60 °C
ECG_2.1 Tc point temperature for lifespa
55 °C
ECG_2.2 Tc point temperature for lifespa
65 °C
ECG_2.3 Tc point temperature for lifespa
70 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
100000 h
ECG_3.3 Temperature dependent lifespan
70000 h
QTz8 1x36
QTz8 2x36
Nominal current
0.32 A
Nominal wattage + Power loss
71.00 W
Luminous flux at 35 °C
3200 lm
Number of lighting outlets
2
ECG_1.1 Ambient temperature for lifespan
50 °C
ECG_1.2 Ambient temperature for lifespan
50 °C
ECG_1.3 Ambient temperature for lifespan
50 °C
ECG_2.1 Tc point temperature for lifespa
60 °C
ECG_2.2 Tc point temperature for lifespa
70 °C
ECG_2.3 Tc point temperature for lifespa
75 °C
ECG_3.1 Temperature dependent lifespan
100000 h
ECG_3.2 Temperature dependent lifespan
80000 h
ECG_3.3 Temperature dependent lifespan
30000 h
Information about Family
Products
Product 




Data sheet  

L 10 W/827

10.00 W  3500 K  Yes  
L 15 W/827

15.00 W  950 lm  2700 K  Yes  
L 15 W/830

15.00 W  950 lm  3000 K  Yes  
L 15 W/840

15.00 W  950 lm  4000 K  Yes  
L 15 W/865

15.00 W  900 lm  6500 K  Yes  
L 16 W/827

16.00 W  1250 lm  2700 K  Yes  
L 16 W/830

16.00 W  1250 lm  3000 K  Yes  
L 16 W/840

16.00 W  1250 lm  4000 K  Yes  
L 18 W/827

18.00 W  1350 lm  2700 K  Yes  
L 18 W/830

18.00 W  1350 lm  3000 K  Yes  
L 18 W/830

18.00 W  1350 lm  3000 K  Yes  
L 18 W/840

18.00 W  4000 K  Yes  
L 18 W/865

18.00 W  1300 lm  6500 K  Yes  
L 18 W/880

18.00 W  1300 lm  8000 K  Yes  
L 23 W/840

23.00 W  1900 lm  4000 K  Yes  
L 30 W/827

30.00 W  2400 lm  2700 K  Yes  
L 30 W/830

30.00 W  2400 lm  3000 K  Yes  
L 30 W/840

30.00 W  2400 lm  4000 K  Yes  
L 30 W/865

30.00 W  2350 lm  6500 K  Yes  
L 36 W/827

36.00 W  3350 lm  2700 K  Yes  
L 36 W/830

36.00 W  3350 lm  3000 K  Yes  
L 36 W/835

36.00 W  3350 lm  3500 K  Yes  
L 36 W/840

36.00 W  3100 lm  4000 K  Yes  
L 36 W/865

36.00 W  3250 lm  6500 K  Yes  
L 36 W/880

36.00 W  3010 lm  8000 K  Yes  
L 38 W/830

38.00 W  3300 lm  3000 K  Yes  
L 38 W/840

38.00 W  3300 lm  4000 K  Yes  
L 58 W/827

58.00 W  5200 lm  2700 K  Yes  
L 58 W/830

58.00 W  5200 lm  3000 K  Yes  
L 58 W/840

58.00 W  5200 lm  4000 K  Yes  
L 58 W/865

58.00 W  5000 lm  6500 K  Yes  
L 58 W/880

58.00 W  4900 lm  8800 K  Yes 